Kamloops Augering Ltd., of Trail, British Columbia, is a trenchless pipe rehab contractor using several trenchless
|For the project, Kamloops used the 24-inch diameter Grundocrack Taurus with a specially fabricated 32-inch front expander with cutting blades.|
Kamloops Augering Ltd., of Trail, British Columbia, is a trenchless pipe rehab contractor using several trenchless techniques including directional drilling, pipe ramming, auger boring, and pipe bursting. Malcolm Bachand, son of Kamloop’s founder Monte Bachand, recently completed one of the most unique and difficult pipe bursting projects the firm ever attempted.
General contractor Marwest Industries, Ltd. in Trail, contracted Kamloops to replace 700 feet (213 m) of 30-inch (762-mm) wood stave pipe with 30-inch (762-mm) High Density Polyethylene (HDPE). For the project, Bachand would use the 24-inch (610-mm) Grundocrack Taurus pipe bursting tool from TT Technologies, Aurora, Illinois.
According to Bachand, the burst was especially challenging. He said, “Cominco had a critical cooling line at its facility in British Colombia that had begun to collapse. To add to the problem, the pipe was 700 feet (213 m) long, extremely deep and was below a highly congested area of the plant with buildings, roads and extensive underground infrastructure. The only solution was to pipe burst the entire run. An open cut option was not feasible. The old cooling line was wood stave pipe and in very rough condition. In many places it had collapsed to half its diameter.”
|The 700 feet of wood stave pipe was burst and replaced with 30- inch HDPE in just 3 1/2 hours.|
TT Technologies Pipe Bursting Specialist, Mike Schwager, explained: “Until the Kamloops project, only a small number of wood stave bursting projects were ever attempted and certainly none of this magnitude and diameter. The thing that makes wood stave so difficult to burst is actually steel. Wood stave pipe is usually bound together with steel bands like a wooden barrel or a continuous steel spiral band.”
In order to effectively burst the steel banding the Kamloops crew used a 32-inch (813-mm) diameter front expander equipped with special cutting blades. This expander was crucial to the success of the project. Schwager said, “We don’t run into situations where we need that large of a tool for bursting that often. The majority of the pipe bursting work currently being done can be more efficiently handled by bursting tools from 3 to 18 inches (76 to 457 mm) in diameter.
A winch system was set up at the end of the run, in a 54- inch (1372-mm) diameter manhole. Once the bursting was completed, the Kamloops crew planned to remove the front expander from the tool and pull the bursting tool out through the new product pipe.
|An example of wood stave pipe. Wood stave was used extensively throughout North and South America in the early 1800s.|
Once the tool arrived at the exit manhole, the Kamloops crew removed the expander without incident or damage to the manhole. The winch was then moved to the entrance pit and a winch-line was rodded through the new HDPE and attached to the tool. The Taurus was pulled back, through the newly installed pipe, to the entrance pit without a problem. The entire project took a mere eight days to complete.
For more information contact Kamloops Augering Ltd., 250-573-7814 or
TT Technologies, e-mail: info@TTtechnologies.com.
See our home page on how to order your subscription. We regret we can only accept orders from Canada and the United States.